In order to achieve long-term stable operation of the data room and improve the operating environment of IT equipment, the temperature of the server cabinet should be controlled within the corresponding range, eliminate local hotspots, and reduce the local temperature of the server cabinet. Let's introduce how to solve the local high heat problem of server cabinets, hoping to be helpful to everyone.
1、 In a computer room without air conditioning, the cabinet can increase heat dissipation and reduce the operating temperature of the equipment by configuring a mesh door and installing a fan at the top.
2、 When there is air conditioning in the computer room, the following measures can be taken to reduce the operating temperature of IT equipment.
Configure a cold channel cabinet system or a hot channel cabinet system. The principle is that controlling the airflow in the data room to save cooling energy consumption and improve server operation stability has become a common measure for data room builders; The separation method of cold and hot channels, the use of wind deflectors and fake panels inside the cabinet to prevent the disorderly flow of hot air, and so on, are also mature and simple technologies. In general, the layout of equipment cabinets in a computer room cannot effectively dissipate heat for equipment located far away from the air conditioning system in the main room. The equipment inside the cabinets operates in a high-temperature environment. To effectively dissipate heat for equipment located far away from the air conditioning system in the main room, either auxiliary air conditioning should be added or the air conditioning temperature in the main room should be lowered, which will increase energy consumption. The cold channel cabinet system or hot channel cabinet system is mainly used in equipment rooms with high equipment density, to eliminate local hot spots and achieve energy conservation and environmental protection through the directional flow of cold air. When the heat generation of a local cabinet is greater than that of other cabinets in the same channel, the problem of heat dissipation can be solved by adding inter column air conditioners next to the corresponding cabinet or adding upward blowing fans and louvers controlling the airflow direction on the perforated electrostatic floor to increase the air intake on the intake side of this cabinet.
This article is organized and published by Jinan Chassis Cabinet. Have you gained some understanding of these contents? For more information, please click on: http://www.tongyuhengcheng.com We will have more exciting content waiting for you to check out.