(1) It is recommended to install the device against the wall or against the wall. The installation foundation plane is required to be flat, the horizontal error of foundation channel steel is 1/1000, and the total length deviation is 3mm.
(2) When the equipment arrives at the destination, first check whether the packing box is complete, or if the equipment is not installed immediately, store it in a dry and clean place.
(3) It is recommended to bolt all conductive parts with Grade 8.8 tension washers.
(4) Connect the cables, and the bottom of the device should be closed to prevent small animals from climbing into the cabinet and causing short circuit accidents.
(5) After installation or adjustment of the device, the following inspections and tests shall be carried out before putting into operation.
Check whether the installation of electrical equipment and control circuit in the equipment meets the requirements of factory drawings.
Manually operate various switches, which shall be flexible and free from abnormalities and jamming.
(3) Check whether the mechanical interlocking mechanism and electrical interlocking device operate correctly and reliably and meet the system requirements.
(4) Check whether the insulation resistance of the main circuit and control circuit meet the specified requirements.
Check whether the electrical equipment set in the device is in good contact and meets the technical conditions of the electrical equipment itself.
Check whether there are foreign matters inside the device and whether the mounting screws of each component are loose.
That's all about the installation, use and maintenance of MNS low-voltage drawer cabinet. If you have any doubts or needs, please visit our website http://www.tongyuhengcheng.com consulting service